State of the Art Dehumidifying System
Refrigeration and Desiccant Rotor Combined
For control the air humidity and air temperature independently in one packaged unit
Fuda offers unique customization to fit every client’s specific applications.
|First Return Airflow(m3/h)||5200|
|Second Return Airflow(m3/h)||2000|
|Rotor Process Airflow(m3/h)||6000|
|Rotor Reactivation Airflow(m3/h)||2000|
|Parameters of Supply Air||T＝12℃, RH≤20%|
|Reactivation Steam Consumption (0.4mPa) (kg/h)||90|
|Reactivation Fan Power(kw)||2.2|
|Driving Motor Power(kw)||0.1|
Chilled Water Consumption
|ESP(External Static Pressure) (Pa)||600|
Outside air is drawn into the unit using the supply fan. The warm, moist outside air first passes through filters and then the cooling coil where it is cooled. The air then goes through the desiccant wheel where the air is dehumidified and the temperature is raised. At last the air is delivered directly to the space or into an existing air handler.