|Installed Power:||33.95kw||Product Name:||Industrial Dehumidifier|
|Rated Air Flow:||2500m³ /h||Desiccant Rotor:||Sweden Proflute|
|Supply Air:||T=20℃ TL=-40℃||Certification:||ISO9001:2008|
Lithium Battery Low Dew Point Industrial Air Dehumidifier Super Dry Air
Style: Double Wheel Adsorption
Desiccant Rotor: Sweden Proflute
Desiccant Rotor Material: Silica Gel and Molecular Sieve Composite Wheel
Rated Air Flow: 2500m³ /h
Supply Air Parameters: T=20℃ TL=-40℃
Dehumidifier Quality: High
Installed Power: 33.95kw
Voltage: 380V, 3 phase, 50Hz or as customer required
Features: Economical, energy-saving
Usage: Air temperature and humidity control
ZCH-2500 Lithium Battery Industry Low Dew Point Dehumidifier is for air deep drying, which is used for manufacturing spaces and processes that require extremely low humidity levels. It can supply air with dew point less than -60℃ to glove box for the production of lithium batteries.
Supply Air Stream
Outside air is drawn into the unit using the supply fan. The warm, moist outside air first passes through filters and then the cooling coil where it is cooled. The air then goes through the first desiccant wheel where the air is dehumidified and the temperature is raised. After the medium cooling, the air is further dehumidified by the second desiccant wheel. At last the air is delivered directly to the space or into an existing air handler.
Exhaust Air Stream
Exhaust air is used to provide energy recovery for the desiccant wheel and is drawn into the unit using the exhaust fan. The air filtered and then heated and humidified during the energy recovery process. The air is then heated while passing through the regeneration coil. The heated air removes the moisture that the desiccant wheel adsorbs from the process air stream.
|Process Airflow||3125m3/h(totally fresh air)|
|Supply Airflow||2500 m3/h|
|Parameter of Output Air||TL≤-40℃|
|Rotor Regeneration Airflow||First Rotor||Second Rotor|
|Regeneration Steam Consumption(0.4mPa)||52Kg/h||32Kg/h|
|Regeneration Fan Power||1.1kw||/|
|Driving Motor Power||0.1kw||0.1kw|
|Dehumidifying Fan Power||3.0kw|
|Compressor Cooling Load||9.5kw|
|Water Cooling Load||94.3kw|
|Chilled Water Consumption(T≤7℃)||16.2T/h|
We can provide the technical design for dehumidification according to your requirements.
Contact Person: Ms. Connie