|Desiccant Rotor:||Sweden Proflute||Installed Power:||14.49kw|
|Product Name:||Air Conditioner Dehumidifier||Rated Air Flow:||1500m³/h|
|Desiccant Material:||Silica Gel Rotor||Supply Air:||T=20℃ RH=30%|
Dry Air Systems Dehumidifier,
Industrial Air Dehumidifier
Desiccant Rotor Dehumidifier with Air Conditioner , Aluminum Alloy Frame
Style: Refrigeration combined Wheel
Desiccant Rotor: Sweden Proflute
Desiccant Rotor Material: Silica Gel Wheel
Rated Air Flow: 1500m³ /h
Supply Air Parameters: T=20℃ RH=30%
Dehumidifier Quality: High
Installed Power: 14.49kw
Voltage: 380V, 3 phase, 50Hz or customized
Features: Economical, energy-saving
Usage: Air temperature and humidity control
ZCB Series Air Conditioner Dehumidifier removes humidity using both refrigeration and a desiccant rotor, so it can both control the humidity and temperature of the air independently in one packaged unit.
Supply Air Stream
Outside air is drawn into the unit using the supply fan. The warm, moist outside air first passes through filters and then the cooling coil where it is cooled. The air then goes through the desiccant wheel where the air is dehumidified and the temperature is raised. At last the air is delivered directly to the space or into an existing air handler.
Exhaust Air Stream
Exhaust air is used to provide energy recovery for the desiccant wheel and is drawn into the unit using the exhaust fan. The air filtered and then heated and humidified during the energy recovery process. The air is then heated while passing through the regeneration coil. The heated air removes the moisture that the desiccant wheel adsorbs from the process air stream.
Total Process Airflow
Rotor Regeneration Airflow
Parameters of Output Air
The Power of Regeneration Fan
The Power of Blower
The Power of Driving Motor
We can provide the technical design and suitable equipment for dehumidification according to your requirements.
Contact Person: Ms. Connie